Would you enter a building if you were told as you stepped in that in the event of a fire there was a chance that the extinguishing system wouldn’t put it out because the fire couldn’t be contained?
No! People expect, and rightfully so, that in the event of a fire the extinguishing systems would be in full working order to do just that – extinguish. Given that the gaseous systems are designed specifically to the individual need of that room, building e.t.c, then a leak sites in the room could meant that the comparted area couldn’t withhold the fire. The technology exists right now to support Door Fan Testing in providing a holistic and thorough integrity test of critical infrastructure.
Regulatory Requirements un-Ravelled
APPROVED DOCUMENT B (ADB)
The regulations demand that compartmentation is upheld for the safety of the individuals, who entrust their lives into its integrity. Approved document B, Fire Safety, Volume 2, Buildings other than dwelling house states that: 8.0 Every compartment wall should form a complete barrier to fire between the compartments they separate. 8.35 – any stairway or other shaft passing directly from one compartment to another should be enclosed in a protected shaft so as to delay or prevent the spread of fire between compartments.
We will lead with some extracts from the regulations which is why this paper argues that the industry is sometimes minimally compliant or even non-compliant due to a lack of understanding of fire systems and their connection to compartmentation. This blog calls for a more holistic approach to fire safety.
To understand how fire resistant a compartment is, an inspection of the overall condition of the existing fire compartments is needed, as well as an assessment of the condition and effectiveness of the sealing of wall/soffit interfaces and an inspection of existing fire seals applied to service penetrations through fire compartment lines. Issues in the quality of compartmentation walls can come from maintenance, minor works and refurbishments. Contractors carrying out such tasks can occasionally destroy the compartmentation integrity of the wall, floor or ceilings if they were unaware that the area is a comparted space (as shown in the below image). Therefore, following maintenance it is “good practice” to ensure the fire resistance of walls, floors and ceilings and to safeguard again if necessary.
Ultrasonic room integrity testers provide interpretation of the fire resistance of the desired locations, labelling them either airtight or giving an indication of the overall leakage of the room. The advantages of being able to accurately detect the exact leak locations and size are self-evident when considered alongside the resistance to collapse and transfer of excessive heat. In a case where there is too much leakage in a room, the ultrasonic room integrity tester is an unrivalled ideal for the rapid and accurate identification of these sites so that they can be sealed. It is lightweight, fast and easy to use, allowing leak site detection to increase its operational efficiency and speed to a degree that has never been seen thus far in the Fire Industry.
Case Study: Oxygen Reduction System - Data Centre, England 2018
Oxygen Reduction System and Need for Monitoring: Oxygen Reduction system works by taking Nitrogen from the air outdoors and pumping this into the room consistently in order to suppress oxygen levels, down to the level where combustion can no longer occur. To ensure the system works safely and efficiently, room integrity is of utmost important for two reasons: (1) A properly sealed room will contain the Nitrogen for a longer period of time, therefore putting less work on the air compressor in order to save energy. (2) If Nitrogen starts to leak from the Server Room, there are safety concerns over where this Nitrogen would leak to as it has the potential to harm occupants in other rooms if the Nitrogen leaks into their room and the oxygen levels were unmonitored.
Testing of the Server Room: The Server Room had an area of about 91 metres square. Several areas were tested with an ultrasonic room integrity tester where leakage was probable and the readings were noted on the drawings. These were the doors, vents, cable penetrations and also sections of the wall where gaps were visible.
Results: The Portascanner® 520 tester identified the main source of leaks for the room, the doors, where full readings were clearly detected. Multiple air vents in the room were also improperly sealed and some leakage was found into the external room. Cable penetrations leading to the area outside the Server Room were also found to be leaking.
Conclusions: Once the required maintenance was conducted and assuming no changes were made to the room, it is safe to assume that the room retains its integrity, thus comply and exceed current ISO 14520 regulations requiring periodic inspections of room integrity whereby visual inspection is usually specified and is not sufficient. The most suitable way to address periodic inspections is through the use of ultrasound.
Coltraco Ultrasonics are a world leading British Manufacturer of Ultrasonic Technology in core areas of watertight & room integrity and gaseous fire suppression systems. Coltraco Ultrasonics are award winning, as Innovate UK Best of British Innovator 2017, Seatrade Cruise Award Supplier of the Year 2017, SHE Award Fire Innovation of the Year Award 2018, amongst many others.
Keywords:Room Integrity, Compartmentation, ISO14520, Ultrasonic Room Integrity Tester